Ideta, Shinichiro*; Johnston, S.*; Yoshida, Teppei*; Tanaka, Kiyohisa*; Mori, Michiyasu; Anzai, Hiroaki*; Ino, Akihiro*; Arita, Masashi*; Namatame, Hirofumi*; Taniguchi, Masaki*; et al.
Physical Review Letters, 127(21), p.217004_1 - 217004_6, 2021/11
Ono, Masato; Iigaki, Kazuhiko; Sawahata, Hiroaki; Shimazaki, Yosuke; Shimizu, Atsushi; Inoi, Hiroyuki; Kondo, Toshinari; Kojima, Keidai; Takada, Shoji; Sawa, Kazuhiro
Journal of Nuclear Engineering and Radiation Science, 4(2), p.020906_1 - 020906_8, 2018/04
On March 11th, 2011, the 2011 off the Pacific coast of Tohoku Earthquake of magnitude 9.0 occurred. When the great earthquake occurred, the High Temperature Engineering Test Reactor (HTTR) had been stopped under the periodic inspection and maintenance of equipment and instruments. A comprehensive integrity evaluation was carried out for the HTTR facility because the maximum seismic acceleration observed at the HTTR exceeded the maximum value of design basis earthquake. The concept of comprehensive integrity evaluation is divided into two parts. One is the "visual inspection of equipment and instruments". The other is the "seismic response analysis" for the building structure, equipment and instruments using the observed earthquake. All equipment and instruments related to operation were inspected in the basic inspection. The integrity of the facilities was confirmed by comparing the inspection results or the numerical results with their evaluation criteria. As the results of inspection of equipment and instruments associated with the seismic response analysis, it was judged that there was no problem for operation of the reactor, because there was no damage and performance deterioration. The integrity of HTTR was also supported by the several operations without reactor power in cold conditions of HTTR in 2011, 2013 and 2015. Additionally, the integrity of control rod guide blocks was also confirmed visually when three control rod guide blocks and six replaceable reflector blocks were taken out from reactor core in order to change neutron startup sources in 2015.
Sato, Junya; Kikuchi, Hiroshi*; Kato, Jun; Sakakibara, Tetsuro; Matsushima, Ryotatsu; Sato, Fuminori; Kojima, Junji; Nakazawa, Osamu
QST-M-8; QST Takasaki Annual Report 2016, P. 62, 2018/03
no abstracts in English
Nakajima, Kenji; Kawakita, Yukinobu; Ito, Shinichi*; Abe, Jun*; Aizawa, Kazuya; Aoki, Hiroyuki; Endo, Hitoshi*; Fujita, Masaki*; Funakoshi, Kenichi*; Gong, W.*; et al.
Quantum Beam Science (Internet), 1(3), p.9_1 - 9_59, 2017/12
The neutron instruments suite, installed at the spallation neutron source of the Materials and Life Science Experimental Facility (MLF) at the Japan Proton Accelerator Research Complex (J-PARC), is reviewed. MLF has 23 neutron beam ports and 21 instruments are in operation for user programs or are under commissioning. A unique and challenging instrumental suite in MLF has been realized via combination of a high-performance neutron source, optimized for neutron scattering, and unique instruments using cutting-edge technologies. All instruments are/will serve in world-leading investigations in a broad range of fields, from fundamental physics to industrial applications. In this review, overviews, characteristic features, and typical applications of the individual instruments are mentioned.
Ono, Masato; Iigaki, Kazuhiko; Shimazaki, Yosuke; Shimizu, Atsushi; Inoi, Hiroyuki; Tochio, Daisuke; Hamamoto, Shimpei; Nishihara, Tetsuo; Takada, Shoji; Sawa, Kazuhiro; et al.
Proceedings of 24th International Conference on Nuclear Engineering (ICONE-24) (DVD-ROM), 12 Pages, 2016/06
On March 11th, 2011, the Great East Japan Earthquake of magnitude 9.0 occurred. When the great earthquake occurred, the HTTR had been stopped under the periodic inspection and maintenance of equipment and instrument. In the great earthquake, the maximum seismic acceleration observed at the HTTR exceeded the maximum value in seismic design. The visual inspection of HTTR facility was carried out for the seismic integrity conformation of HTTR. The seismic analysis was also carried out using the observed earthquake motion at HTTR site to confirm the integrity of HTTR. The concept of comprehensive integrity evaluation for the HTTR facility is divided into two parts. One is the inspection of equipment and instrument. The other is the seismic response analysis using the observed earthquake. For the basic inspections of equipment and instrument were performed for all them related to the operation of reactor. The integrity of the facilities is confirmed by comparing the inspection results or the numerical results with their evaluation criteria. As the result of inspection of equipment and instrument and seismic response analysis, it was judged that there was no problem to operate the reactor, because there was no damage and performance deterioration, which affects the reactor operation. The integrity of HTTR was also supported by the several operations without reactor power in cold conditions of HTTR in 2011, 2013 and 2015.
Nishikiori, Ryo; Kojima, Atsushi; Hanada, Masaya; Kashiwagi, Mieko; Watanabe, Kazuhiro; Umeda, Naotaka; Tobari, Hiroyuki; Yoshida, Masafumi; Ichikawa, Masahiro; Hiratsuka, Junichi; et al.
Plasma and Fusion Research (Internet), 11, p.2401014_1 - 2401014_4, 2016/03
One of critical issues for high-energy high-current beam acceleration in ITER and JT-60SA is the high voltage holding which is dominated by vacuum discharges. The past results suggest that vacuum discharge occurs beyond the threshold of the dark current. The dark current can be derived from F-N theory where electric field enhancement factor beta is included. Though, beta could only be evaluated from the experiment previously. Therefore, the method to decide beta without experiment is required. This time dark currents were measured at three different areas to compare beta in different electric field. As a result, the effective electric field E, where E is average electric field, were found to be almost constant for different areas although the beta is largely different. By applying E, beta can be evaluated analytically, leading to the analytical prediction of the dark current and voltage holding capability without the measurements.
Hiratsuka, Junichi; Hanada, Masaya; Kojima, Atsushi; Umeda, Naotaka; Kashiwagi, Mieko; Miyamoto, Kenji*; Yoshida, Masafumi; Nishikiori, Ryo; Ichikawa, Masahiro; Watanabe, Kazuhiro; et al.
Review of Scientific Instruments, 87(2), p.02B137_1 - 02B137_3, 2016/02
To understand the physics of the negative ion extraction/acceleration, the heat load density profile on the acceleration grid has been firstly measured in the ITER prototype accelerator where the negative ions are accelerated to 1 MeV with five acceleration stages. In order to clarify the profile, the peripheries around the apertures on the acceleration grid were separated into thermally insulated 34 blocks with thermocouples. The spatial resolution is as low as 3 mm and small enough to measure the tail of the beam profile with a beam diameter of 16 mm. It was found that there were two peaks of heat load density around the aperture. These two peaks were also clarified to be caused by the intercepted negative ions and secondary electrons from detailed investigation by changing the beam optics and gas density profile. This is the first experimental result, which is useful to understand the trajectories of these particles.
Yoshida, Masafumi; Hanada, Masaya; Kojima, Atsushi; Kashiwagi, Mieko; Umeda, Naotaka; Hiratsuka, Junichi; Ichikawa, Masahiro; Watanabe, Kazuhiro; Grisham, L. R.*; Tsumori, Katsuyoshi*; et al.
Review of Scientific Instruments, 87(2), p.02B144_1 - 02B144_4, 2016/02
Time evolution of spatial profile of negative ion production during an initial conditioning phase has been experimentally investigated in the JT-60 negative ion source. Up to 0.4 g Cs injection, there is no enhancement of the negative ion production and no observation of the Cs emission signal in the source, suggesting the injected Cs is mainly deposited on the water-cooled wall near the nozzle. After 0.4 g Cs injection, enhancement of the negative ion production appeared only at the central segment of the PG. The calculation of the Cs neutral/ion trajectories implied that a part of Cs was ionized near the nozzle and was transported to this area. The expansion of the area of the surface production was saturated after ~2 g Cs injection corresponding to 6000 s discharge time. From the results, it is found that Cs ionization and its transport plays an important role for the negative ion production.
Kojima, Atsushi; Hanada, Masaya; Tobari, Hiroyuki; Nishikiori, Ryo; Hiratsuka, Junichi; Kashiwagi, Mieko; Umeda, Naotaka; Yoshida, Masafumi; Ichikawa, Masahiro; Watanabe, Kazuhiro; et al.
Review of Scientific Instruments, 87(2), p.02B304_1 - 02B304_5, 2016/02
Optimization techniques of the vacuum insulation design have been developed in order to realize a reliable voltage holding capability of Multi-Aperture Multi-Grid accelerators for giant negative ion sources for nuclear fusion. In this method, the nested multilayer configuration of each acceleration stage in the MAMuG accelerator can be uniquely designed to satisfy the target voltage within given boundary conditions. The evaluation of the voltage holding capabilities of each acceleration stages were based on the past experimental results of the area effect and the multi-aperture effect on the voltage holding capability. Moreover, total voltage holding capability of multi-stage was estimated by taking the multi-stage effect into account, which was experimentally obtained in this time. In this experiment, the multi-stage effect appeared as the superposition of breakdown probabilities in each acceleration stage, which suggested that multi-stage effect can be considered as the voltage holding capability of the single acceleration gap having the total area and aperture. The analysis on the MAMuG accelerator for JT-60SA agreed with the past gap-scan experiments with an accuracy of less than 10% variation.
Hanada, Masaya; Kojima, Atsushi; Tobari, Hiroyuki; Nishikiori, Ryo; Hiratsuka, Junichi; Kashiwagi, Mieko; Umeda, Naotaka; Yoshida, Masafumi; Ichikawa, Masahiro; Watanabe, Kazuhiro; et al.
Review of Scientific Instruments, 87(2), p.02B322_1 - 02B322_4, 2016/02
In International Thermo-nuclear Experimental Reactor (ITER) and JT-60 Super Advanced (JT-60 SA), the D ion beams of 1 MeV, 40 A and 0.5 MeV, 22 A are required to produce 3600 s and 100 s for the neutral beam injection, respectively. In order to realize such as powerful D ion beams for long duration time, Japan Atomic Energy Agency (JAEA) has energetically developed cesium (Cs)-seeded negative ion sources (CsNIS) and electro-static multi-aperture and multi-stage accelerators (MAMuG accelerator) which are chosen as the reference design of ITER and JT-60 SA. In the development of the CsNIS, a 100s production of the H ion beam has been demonstrated with a beam current of 15 A by modifying the JT-60 negative ion source. At the higher current, the long pulse production of the negative ions has been tried by the mitigation of the arcing in the plasma inside the ion source. As for the long pulse acceleration of the negative ions in the MAMuG accelerator, the beam steering angle has been controlled to reduce the power loading of the acceleration grids A pulse duration time has been significantly extended from 0.4 s to 60 s at reasonable beam power for ITER requirement. The achieved pulse duration time is limited by the capacity of the power supplies in the test stand. In the range of 60 s, there are no degradations of beam optics and voltage holding capability in the accelerator. It leads to the further extension of the pulse duration time at higher power density. This paper reports the latest results of development on the negative ion source and accelerator at JAEA.
Yoshida, Masafumi; Hanada, Masaya; Kojima, Atsushi; Kashiwagi, Mieko; Grisham, L. R.*; Hatayama, Akiyoshi*; Shibata, Takanori*; Yamamoto, Takashi*; Akino, Noboru; Endo, Yasuei; et al.
Fusion Engineering and Design, 96-97, p.616 - 619, 2015/10
In JT-60 Super Advanced for the fusion experiment, 22A, 100s negative ions are designed to be extracted from the world largest ion extraction area of 450 mm 1100 mm. One of the key issues for producing such as high current beams is to improve non-uniform production of the negative ions. In order to improve the uniformity of the negative ions, a tent-shaped magnetic filter has newly been developed and tested for JT-60SA negative ion source. The original tent-shaped filter significantly improved the logitudunal uniformity of the extracted H ion beams. The logitudinal uniform areas within a 10 deviation of the beam intensity were improved from 45% to 70% of the ion extraction area. However, this improvement degrades a horizontal uniformity. For this, the uniform areas was no more than 55% of the total ion extraction area. In order to improve the horizontal uniformity, the filter strength has been reduced from 660 Gasuscm to 400 Gasuscm. This reduction improved the horizontal uniform area from 75% to 90% without degrading the logitudinal uniformity. This resulted in the improvement of the uniform area from 45% of the total ion extraction areas. This improvement of the uniform area leads to the production of a 22A H ion beam from 450 mm 1100 mm with a small amount increase of electron current of 10%. The obtained beam current fulfills the requirement for JT-60SA.
Adachi, Taihei*; Ikedo, Yutaka*; Nishiyama, Kusuo*; Yabuuchi, Atsushi*; Nagatomo, Takashi*; Strasser, P.*; Ito, Takashi; Higemoto, Wataru; Kojima, Kenji*; Makimura, Shunsuke*; et al.
JPS Conference Proceedings (Internet), 8, p.036017_1 - 036017_4, 2015/09
Kojima, Atsushi; Umeda, Naotaka; Hanada, Masaya; Yoshida, Masafumi; Kashiwagi, Mieko; Tobari, Hiroyuki; Watanabe, Kazuhiro; Akino, Noboru; Komata, Masao; Mogaki, Kazuhiko; et al.
Nuclear Fusion, 55(6), p.063006_1 - 063006_9, 2015/06
Significant progresses in the extension of pulse durations of powerful negative ion beams have been made to realize the neutral beam injectors for JT-60SA and ITER. In order to overcome common issues of the long pulse production/acceleration of negative ion beams in JT-60SA and ITER, the new technologies have been developed in the JT-60SA ion source and the MeV accelerator in Japan Atomic Energy Agency. As for the long pulse production of high-current negative ions for JT-60SA ion source, the pulse durations have been successfully increased from 30 s at 13 A on JT-60U to 100 s at 15 A by modifying the JT-60SA ion source, which satisfies the required pulse duration of 100 s and 70% of the rated beam current for JT-60SA. This progress was based on the R&D efforts for the temperature control of the plasma grid and uniform negative ion productions with the modified tent-shaped filter field configuration. Moreover, the each parameter of the required beam energy, current and pulse has been achieved individually by these R&D efforts. The developed techniques are useful to design the ITER ion source because the sustainment of the cesium coverage in large extraction area is one of the common issues between JT-60SA and ITER. As for the long pulse acceleration of high power density beams in the MeV accelerator for ITER, the pulse duration of MeV-class negative ion beams has been extended by more than 2 orders of magnitude by modifying the extraction grid with a high cooling capability and a high-transmission of negative ions. A long pulse acceleration of 60 s has been achieved at 70 MW/m (683 keV, 100 A/m) which has reached to the power density of JT-60SA level of 65 MW/m.
Kojima, Atsushi; Hanada, Masaya; Yoshida, Masafumi; Umeda, Naotaka; Hiratsuka, Junichi; Kashiwagi, Mieko; Tobari, Hiroyuki; Watanabe, Kazuhiro; Grisham, L. R.*; NB Heating Technology Group
AIP Conference Proceedings 1655, p.060002_1 - 060002_10, 2015/04
In this paper, the recent activities on the new test stand are reported toward demonstration of the long pulse production for 22A, 100s negative ion beams. As for the temperature control of the plasma grid, a prototype of the grid with cooling/heating by circulating a high-temperature fluorinated fluid has been improved to cover the full extraction area by using 5 segments of the PG. These grids were found to have a capability to control the temperature with a time constant of 10s as well as the prototype grid. As a result, 15A negative ion beams for 100s have been achieved.
Umeda, Naotaka; Kojima, Atsushi; Kashiwagi, Mieko; Tobari, Hiroyuki; Hiratsuka, Junichi; Watanabe, Kazuhiro; Dairaku, Masayuki; Yamanaka, Haruhiko; Hanada, Masaya
AIP Conference Proceedings 1655, p.050001_1 - 050001_10, 2015/04
For ITER neutral beam system, negative deuterium ion beam of 1 MeV, 40 A (current density of 200 A/m) is required for 3600 s. To demonstrate ITER relevant negative ion beam acceleration, beam acceleration test has been carried out at MeV test facility in JAEA. The present target is H ion beam acceleration up to 1 MeV with 200 A/m for 60 s, which beam energy and pulse length are the present facility limit. To extend pulse duration time up to facility limit at high power density beam, new extraction grid has been developed with high cooling capability, which electron suppression magnet is placed under cooling channel. In addition, the aperture size of the electron suppression grid is enlarged from 14 mm to 16 mm and the aperture displacement is modified to reduce collision of negative ion beam on the grid. By these modifications, total grid power loading has reduced from 14% to 11%. As a result, beam acceleration up to 60 s which is the facility limit, has achieved at 700 kV, 100 A/m of negative ion beam without breakdown.
Hiratsuka, Junichi; Hanada, Masaya; Umeda, Naotaka; Kojima, Atsushi; Kashiwagi, Mieko; Watanabe, Kazuhiro; Tobari, Hiroyuki; Yoshida, Masafumi
Plasma and Fusion Research (Internet), 10(Sp.2), p.3405045_1 - 3405045_4, 2015/04
To produce high current density ( 200 A/m), high-energy ( 1 MeV) negative ion beams for long pulse duration time (1 hour) for International Thermo-nuclear Experimental Reactor (ITER), the suppression of the direct interception of the negative ions with the grids has been carefully investigated with studying the deflection angle by aperture displacement technique. The non-linear dependence of the deflection angle appears at the aperture diameter of 14 mm on a steering control grid (SCG). From this dependence, the aperture diameter and the offset distance of the SCG has been designed to be 16 mm and 0.7 mm, respectively and tested in a prototype accelerator for ITER. Each of the beamlets on the multiple apertures is properly steered with compensation of the deflection due to the residual magnetic field in the accelerator and the grid power loading was significantly reduced. It resulted in a 10% enhancement of the accelerated beam current.
Akino, Noboru; Endo, Yasuei; Hanada, Masaya; Kawai, Mikito*; Kazawa, Minoru; Kikuchi, Katsumi*; Kojima, Atsushi; Komata, Masao; Mogaki, Kazuhiko; Nemoto, Shuji; et al.
JAEA-Technology 2014-042, 73 Pages, 2015/02
According to the project plan of JT-60 Super Advanced that is implemented as an international project between Japan and Europe, the neutral beam (NB) injectors have been disassembled. The disassembly of the NB injectors started in November, 2009 and finished in January, 2012 without any serious problems as scheduled. This reports the disassembly activities of the NB injectors.
Komata, Masao; Shimizu, Tatsuo; Ozeki, Masahiro; Kojima, Atsushi; Hanada, Masaya
JAEA-Technology 2014-041, 50 Pages, 2015/01
In JT-60 Super Advanced, the machine for nuclear fusion research with superconducting magnets for long pulse operation, the negative-ion-base neutral beam injector is required to extend the pulse duration time 10 s to 100 s. In order to realize the long-pulse N-NB injector, the control system of the power supplies for the negative ion source has been newly developed. The control system with use of the versatile devices such as PLC was designed for an ease extension of the functions. Since the control system should have the many different functions which require the wide range of the sampling time of 1 milli-second to 10, all of the functions are performed by distributing PLCs for each of the function. The developed control system has been applied in the tests of the JT-60 negative ion source, where a 100 s negative ion beam has been successfully produced. Through this test, the controllability of this system has been confirmed to be feasible for JT-60SA operation.
Takahashi, Hiroki; Narita, Takahiro; Nishiyama, Koichi; Usami, Hiroki; Sakaki, Hironao; Kasugai, Atsushi; Kojima, Toshiyuki*
Proceedings of 11th Annual Meeting of Particle Accelerator Society of Japan (Internet), p.799 - 802, 2014/10
no abstracts in English
Kojima, Atsushi; Hanada, Masaya; Yoshida, Masafumi; Tobari, Hiroyuki; Kashiwagi, Mieko; Umeda, Naotaka; Watanabe, Kazuhiro; Grisham, L. R.*
Review of Scientific Instruments, 85(2), p.02B312_1 - 02B312_5, 2014/02
The negative ion source for JT-60SA is designed to produce high power and long pulse beams with a beam energy of 500 keV, a negative ion current of 22A and a pulse duration of 100s. One of the key issues toward long pulse production of such high-current beams is the control of the surface temperature on the plasma grid (PG) where cesium is layered. In order to optimize cesium layer on PG for long pulse duration, we have developed an actively cooled PG where fluorinated fluids having high boiling point of 270C is circulated. While the surface temperature of the PG in the JT-60 negative ion source has been kept at 170C for 100s with ramp-up time of 7s, stable long pulse beam extractions of 100s have been obtained. This current density is 90% of the required current density for JT-60 SA. The further increase of the current density is expected by optimizing the arc discharge power.