Aso, Tomokazu; Tatsumoto, Hideki*; Otsu, Kiichi*; Kawakami, Yoshihiko*; Komori, Shinji*; Muto, Hideki*; Takada, Hiroshi
JAEA-Technology 2019-013, 77 Pages, 2019/09
At Materials and Life Science experimental Facility (MLF) of the Japan Proton Accelerator Research Complex (J-PARC), a 1-MW pulsed spallation neutron source is equipped with a cryogenic hydrogen system which circulates liquid hydrogen (20 K and 1.5 MPa) to convert high energy neutrons generated at a mercury target to cold neutrons at three moderators with removing nuclear heat of 3.8 kW deposited there. The cryogenic system includes an accumulator with a bellows structure in order to absorb pressure fluctuations generated by the nuclear heat deposition in the system. Welded inner bellows of the first accumulator was failured during operation, forcing us to improve the accumulater to have sufficient pressure resistance and longer life-time. We have developed elemental technologies for manufacturing welded bellows of the accumulator by a thick plate with high pressure resistance, succeeding to find optimum welding conditions. We fabricated a prototype bellows block and carried out an endurance test by adding a pressure change of 2 MPa repeatedly. As a result, the prototype bellows was successfully in use exceeding the design life of 10,000 times. Since distortions given during welding and assembling affect functionality and lifetime of the bellows, we set the levelness of each element of the bellows as within 0.1. The improved accumulator has already been in operation for about 25,000 hours as of January 2019, resulting that the number of strokes reached to 16,000. In July 2018, we demonstrated that the accumulator could suppress the pressure fluctuation generated by the 932 kW beam injection as designed. As current operational beam power is 500 kW, the current cryogenic hydrogen system could be applicable for stable operation at higher power in the future.
Ono, Masato; Kozawa, Takayuki; Fujimoto, Nozomu*
JAEA-Technology 2019-012, 15 Pages, 2019/09
The High Temperature Engineering Test Reactor has a neutron source of Cf to start up the reactor and to confirm count rates of wide range monitors. The half-life of Cf is short, about 2.6 years, so it is necessary to replace at an appropriate time. In order to estimate the period to replace, it is necessary to consider not only the half-life but also the fluctuation of the count rate of the wide range monitor to prevent alarm. For that reason, the method has been derived to predict a minimum count rate from relationship between the count rate and the standard deviation of the count rate of the wide range monitors. As a result of predicting the count rate using this method, it was found that the minimum count rate reaches to 3.0cps in 2022 and 1.5 cps in 2024. Therefore, it is necessary to exchange Cf by 2024.
Journal of Nuclear Science and Technology, 56(9-10), p.831 - 841, 2019/09
The insoluble Cs particles (Type A) were firstly observed in Tsukuba-city on the morning of March 15. The particles have been considered to be generated in RPV of Unit 2 by evaporation/condensation based on the measured Cs/Cs ratio and the core temperatures of each unit. However, the Type A particles with smaller diameter than the Type B particles of Unit 1 origin, are covered by almost pure silicate glass and have a trace of the quenching. This indicates that the particles could have been generated due to the melting of the HEPA filter in SGTS by the fire of H detonation at Unit 3, and atomization followed by quenching of the molten materials by air blast of the explosion. Although the particles were mostly dispersed to the sea because of the wind direction, some of them deposited onto the lower elevation of R/B at Unit 3, could have been subsequently re-suspended and released into the environment, by the steam flow in the R/B caused by restart of the Unit 3 core cooling water injection at 2:30 of March 15.
Wakui, Takashi; Ishii, Hideaki*; Naoe, Takashi; Kogawa, Hiroyuki; Haga, Katsuhiro; Wakai, Eiichi; Takada, Hiroshi; Futakawa, Masatoshi
Materials Transactions, 60(6), p.1026 - 1033, 2019/06
The mercury target has large size as 188.8.131.52 m. In view of reducing the amount of wastes, we studied the structure so that the fore part could be separated. The flange is required to have high seal performance less than 110 Pa m/s. Invar with low thermal expansion is a candidate. Due to its low stiffness, however, the flange may deform when it is fastened by bolts. Practically invar is reinforced with stainless steel where all interface between them has to be bonded completely with the HIP bonding. In this study, we made specimens at four temperatures and conducted tensile tests. The specimen bonded at 973 K had little diffusion layer, and so fractured at the interface. The tensile strength reduced with increasing the temperature, and the reduced amount was about 10% at 1473 K. The analyzed residual stresses near the interface increased by 50% at maximum. Then, we concluded that the optimum temperature was 1173 K.
Proceedings of 27th International Conference on Nuclear Engineering (ICONE-27) (Internet), 6 Pages, 2019/05
no abstracts in English
Chino, Masamichi*; Nagai, Haruyasu
Environmental Contamination from the Fukushima Nuclear Disaster; Dispersion, Monitoring, Mitigation and Lessons Learned, p.50 - 61, 2019/00
Temporal variations in the amount of radionuclides released into the atmosphere during the Fukushima Daiichi Nuclear Power Station accident and their atmospheric dispersion are essential to evaluate the environmental impacts and resultant radiological doses to the public. We have estimated the atmospheric releases during the accident by comparing measurements with calculations by atmospheric deposition model. UNSCEAR compared several estimated source terms and used our source term for estimating levels of radioactive material in the terrestrial environment and doses to the public. To improve our source term, we recently made detailed source term estimation by using additional monitoring data and WSPEEDI including new deposition scheme.
Proceedings of 13th International Symposium on Advanced Science and Technology in Experimental Mechanics (13th ISEM'18) (USB Flash Drive), 6 Pages, 2018/10
Issues on the engineering technologies relating to high-power spallation neutron sources with liquid metals are introduced. The present status on research activities and results was reviewed.
Tamaki, Hitoshi; Ishikawa, Jun; Sugiyama, Tomoyuki; Maruyama, Yu
Proceedings of Asian Symposium on Risk Assessment and Management 2018 (ASRAM 2018) (USB Flash Drive), 6 Pages, 2018/10
In the accidents at Fukushima Dai-ichi Nuclear Power Station, Tsunami caused loss of electric power supply and this event led to core melt and failure of Containment vessel. Finally, fission products were released to the environment. Currently, the activities for understanding of accident progressions are carried out based on the measured data during the accident, accident progression analysis using integrated severe accident analysis codes and investigation of inside of reactor buildings and containment vessels. On the other hand, there are some research activities with combination of accident progression analysis and accident consequence analysis. In Japan Atomic Energy Agency (JAEA), the research project of combination of these analyses using the computational simulation codes has been started. The results obtained from the combination analysis are expected to have broad width of uncertainty because of many uncertainty factors in this combined analysis. In order to perform the analysis efficiently, sensitivity analysis for failure location on containment vessel and its failure size were carried out by THALES2/KICHE developed by JAEA at first. This analysis was performed on unit 1, since it was the first plant to release radioactive materials to the environment during the accident and its consequence had no effect from other plants. The authors focused on the failure of containment vessel head flange, penetration seal and vacuum breaker pipe, and possibility of partial open of vent valve based on the investigations of reactor building inside performed by TEPCO. This paper presents the results obtained from this sensitivity analysis.
Harada, Masahide; Teshigawara, Makoto; Oi, Motoki; Klinkby, E.*; Zanini, L.*; Batkov, K.*; Oikawa, Kenichi; Toh, Yosuke; Kimura, Atsushi; Ikeda, Yujiro
Nuclear Instruments and Methods in Physics Research A, 903, p.38 - 45, 2018/09
Kitatani, Fumito; Tsuchiya, Harufumi; Toh, Yosuke; Hori, Junichi*; Sano, Tadafumi*; Takahashi, Yoshiyuki*; Nakajima, Ken*
KURRI Progress Report 2017, P. 99, 2018/08
Teshigawara, Makoto; Harada, Masahide; Oi, Motoki; Takada, Hiroshi
Journal of Physics; Conference Series, 1021(1), p.012061_1 - 012061_4, 2018/06
At the spallation neutron source of J-PARC, the structural material of moderators and reflector, such as an aluminum alloy, is going to reach to the design value (20 DPA) around 2020 by an accumulation of irradiation-damage. We started the fabrication of the spare moderators and reflector in 2013 with following design of two improvements. The invar joints, such as invar-A6061 and invar- SS316L joints were newly developed to utilize them in the cryogenic multi-layered pipe with 5th annular geometry, improving the fabrication procedure much simple. The Gold-Indium-Cadmium (Au-In-Cd) as a decoupler material is also developed to reduce residual radioactivity of the used components significantly for the decoupled moderator. In this presentation, we will report these results and progress of fabrication.
Plasma and Fusion Research (Internet), 13(Sp.1), p.2505013_1 - 2505013_8, 2018/03
The pulsed spallation neutron source of Japan Proton Accelerator Research Complex (J-PARC) has been supplying users with high intensity and sharp pulse cold neutrons using the moderators with following distinctive features; (1) 100% para-hydrogen for increasing pulse peak intensity with decreasing pulse tail, (2) cylindrical shape with 14 cm diam.12 cm long for providing high intensity neutrons to wide neutron extraction angles of 50.8, (3) neutron absorber made from Ag-In-Cd alloy to make pulse width narrower and pulse tails lower. Actually, it was measured at a low power operation that high neutron intensity of 4.510 n/cm/s/sr could be emitted from the coupled moderator surface for 1-MW operation, and a superior resolution of d/d = 0.035% was achieved at a beamline (BL8) with a poisoned moderator, where d is the d-spacing of reflection. Towards the goal to achieve the target operation at 1-MW for 5000 h in a year, technical developments to mitigate cavitation damages on the target vessel with injecting gas micro-bubbles into mercury target and design improvement of target vessel structure to reducing welds and bolt connections as much as possible are under way.
Teshigawara, Makoto; Ikeda, Yujiro; Oi, Motoki; Harada, Masahide; Takada, Hiroshi; Kakishiro, Masanori*; Noguchi, Gaku*; Shimada, Tsubasa*; Seita, Kyoichi*; Murashima, Daisuke*; et al.
Nuclear Materials and Energy (Internet), 14, p.14 - 21, 2018/01
We developed an Au-In-Cd (AuIC) decoupler material to reduce induced radioactivity instead of Ag-In-Cd one, which has a cut off energy of 1eV. In order to implement it into an actual moderator-reflector assembly, a number of critical engineering issues need to be resolved with regard to large-sized bonding between AuIC and A5083 alloys by the hot isostatic pressing process. We investigated this process in terms of the surface conditions, sizes, and heat capacities of large AuIC alloys. We also show a successful implementation of an AuIC decoupler into a reflector assembly, resulting in a remarkable reduction of radioactivity by AuIC compared to AIC without sacrificing neutronic performance.
Yoshizawa, Atsufumi*; Oba, Kyoko; Kitamura, Masaharu*
Nippon Kikai Gakkai Rombunshu (Internet), 83(856), p.17-00263_1 - 17-00263_17, 2017/12
Hamon, 27(4), p.155 - 158, 2017/11
The pulsed spallation neutron source driven by a high-power accelerator is one of the most powerful apparatus to provide high intensity and high quality neutrons with narrow pulse width for conducting cutting-edge researches in several domains of materials and life science. In this system, proton beams of several kW to MW order extracted from the high power accelerator is injected into a target, which is heavy metal, to generate vast amount of neutrons via the spallation reactions with the target nuclei, and slows down these neutrons to thermal to cold neutrons with a moderator and a reflector. Resultant neutron beams are then supplied to a suit of the state-of-the-art experimental devices. In this paper, mechanism to produce neutron beams and outline of the spallation neutron source, engineering design of a target system such as a mercury target, and technical topics to solve the pitting damage problem of the target vessel which is caused by the pressure wave of up to 40MPa at maximum generated in the mercury by the pulsed proton beam injection are reviewed by referring mainly to the mercury target system of the pulsed spallation neutron source at J-PARC.
Nagai, Haruyasu; Terada, Hiroaki; Tsuzuki, Katsunori; Katata, Genki; Ota, Masakazu; Furuno, Akiko; Akari, Shusaku
EPJ Web of Conferences (Internet), 153, p.08012_1 - 08012_7, 2017/09
In order to assess the radiological dose to the public resulting from the Fukushima Daiichi Nuclear Power Station (FDNPS) accident in Japan, the spatiotemporal distribution of radioactive materials in the environment are reconstructed by computer simulations. In this study, by refining the source term of radioactive materials and modifying the atmospheric dispersion model (ATDM), the atmospheric dispersion simulation of radioactive materials is improved. Then, a database of spatiotemporal distribution of radioactive materials in the air and on the ground surface is developed from the output of the simulation. This database is used in other studies for the dose assessment by coupling with the behavioral pattern of evacuees from the FDNPS accident. The ATDM simulation was improved to use a new meteorological model and sophisticated deposition scheme. Although the improved ATDM simulations reproduced well the Cs deposition pattern in the eastern Japan scale, the reproducibility of deposition pattern was decreased in the vicinity of FDNPS. This result indicated the necessity of further refinement of the source term by optimization to the improved ATDM simulations.
Hidaka, Akihide; Yokoyama, Hiroya
Proceedings of Symposium on Water Chemistry and Corrosion in Nuclear Power Plants in Asia 2017 (AWC 2017) (USB Flash Drive), p.29 - 42, 2017/09
no abstracts in English
Takada, Hiroshi; Haga, Katsuhiro; Teshigawara, Makoto; Aso, Tomokazu; Meigo, Shinichiro; Kogawa, Hiroyuki; Naoe, Takashi; Wakui, Takashi; Oi, Motoki; Harada, Masahide; et al.
Quantum Beam Science (Internet), 1(2), p.8_1 - 8_26, 2017/09
At the Japan Proton Accelerator Research Complex (J-PARC), a pulsed spallation neutron source provides neutrons with high intensity and narrow pulse width to promote researches on a variety of science in the Materials and life science experimental facility. It was designed to be driven by the proton beam with an energy of 3 GeV, a power of 1 MW at a repetition rate of 25 Hz, that is world's highest power level. A mercury target and three types of liquid para-hydrogen moderators are core components of the spallation neutron source. It is still on the way towards the goal to accomplish the operation with a 1 MW proton beam. In this paper, distinctive features of the target-moderator-reflector system of the pulsed spallation neutron source are reviewed.
Hidaka, Akihide; Yokoyama, Hiroya
Journal of Nuclear Science and Technology, 54(8), p.819 - 829, 2017/08
To clarify what happened during the Fukushima accident, the phenomena within RPV and the discussion of ties with the environmental monitoring are very important. However, the previous study has not necessarily advanced until the present that passed almost six years from the accident. The present study investigated I and Cs release behaviors during the late phase of the accident based on I/Cs ratio of the source terms that were recently evaluated backward by WSPEEDI code based on environmental monitoring data. The I release from the contaminated water in the basement of 1F2 and 1F3 reactor buildings was evaluated to be about 10% of I source term. The increase in Cs release from March 21 to 23 and from March 30 to 31 could be explained by the release of CsBO which is formed as a result of chemical reactions of Cs with BC due to re-ascension of the core temperature caused by slight shortage of the core cooling water.
Hidaka, Akihide; Yokoyama, Hiroya
Journal of Nuclear Science and Technology, 54(8), P. i, 2017/08
no abstracts in English